Smoke Stratification - A Matter of Height
FREE Fire Safety Audit
Book your FREE, no-strings-attached Fire Safety Audit to ensure that you’re properly protected from the risk and comply with current fire safety legislation.
STAY SAFE, STAY INFORMED
Get essential insights and updates
in fire safety – straight to your inbox!
IS YOUR FIRE DETECTION SYSTEM USELESS?
THE OVERLOOKED DANGER in Waste Recycling, Logistics, Manufacturing…. and many other industry sectors THAT OPERATES OUT OF HIGH-ROOFED BUILDINGS.
You may have invested in the best smoke detection system money can buy… but it’s totally ineffective if the smoke can’t actually reach it.
Do you have a high-roofed building of over 8 meters? If so, you need to ensure your fire detection system is fit for purpose, because of a hidden danger known as ‘Smoke Stratification’.
Smoke Stratification is a phenomenon that occurs in high-level buildings typical to the waste industry, when rising heat collects in the roof void, creating a layer of air substantially warmer than that beneath. Smoke requires substantial energy to ‘punch’ through this warm layer of air. This means that, in the early stages of a fire, the smoke is too cool to rise through the layer and therefore levels out.
STUDIES SHOW THAT THE FIRST 3 MINUTES OF FIRE ARE THE MOST CRITICAL, SO BY THE TIME EVEN AN ASPIRATING SYSTEM HAS DETECTED THE SMOKE, THERE IS AN INFERNO RAGING BELOW
Studies show that the first 3-5 minutes of a fire are often the most critical. This poses a particular problem to waste management operators, due to the flammable material being processed. If the fire is lefty to develop to sufficient intensity, causing the smoke to force its way through the thermal “layer” to the ceiling-mounted detectors, there could well be an inferno raging below before anything at all is detected.
Suitable detection methods are clearly critical for this high-risk industry, especially in order to counter the effects of smoke stratification and detect fires early in such cases.
We undertook live tests in a typical high-roofed building (roof height 12m), comparing the Araani SmokeCatcher Video Smoke Detection System to a number of ceiling mounted smoke detection systems, including:
- Point-type smoke detectors.
- Beam Detectors.
- Aspirating Detection (HSSD).
In the live tests, the effects of smoke stratification were made clear. Not one of the ceiling mounted smoke detection systems detected anything, whereas the SmokeCatcher Video system activated in just 15 seconds.
The tests highlight the fact that many of the systems fitted to waste recycling facilities are simply not effective enough for the industry and the high fire threat level it faces.
In conclusion, Smoke Stratification – although little known – is one of the greatest obstacles to successful fire detection in waste management and a Video Smoke detection system provides an excellent solution to the problem.
If you’d like to know more about stratification and how your business can overcome it, give us a call on 01234 357357 and we’ll book in a no-obligation chat.
Share this post
Explore Related Content
Fires are often unpredictable, destructive, and can cause massive loss of life. Understanding how fire works can help us prevent it, predict it, and control it. One of the most
Explore Our Video Vault for more Fire Safety Experience
Video Smoke Detection for Waste Recycling
Video Smoke Detection is perfect for a fast response to fires in high roofed buildings and harsh operating conditions.
Real Fire - Smoke Detection in MSW Storage
Watch Smokecatcher detect smoke in an MSW storage building. The smoke is coming through from a fire in the adjoining storage area.
Real Fire - SRF Storage Area
Watch Smokecatcher detect a fire in an SRF Storage bunker. Sadly, the alarm wasn’t responded to and the site lost a 4hr window of opportunity between smoke detection and flames appearing.
Video Smoke Detection for Logistics
Video Smoke Detection overcomes the risks of stratification and other challenges for early fire detection in logistics and storage facilities.
EFW Bunker Fire
Watch Fire Rover detect and suppress a fire in the waste bunker at an EFW facility!
Tipping Hall Fire
See how the Fire Rover detects and suppresses this fire at a clients tipping hall. Note how the smok is spreading out at low leve, rather than rising. This is called ‘stratification’ and is one of the many reasons why roof-mounted smoke detection systems like beam detectors and HSSD is not suitable for many recycling applications.
Battery Storage Fire
Watch the Fire Rover detect and suppress a fire at a battery storage facility. This targeted and intellegent control makes the Fire Rover particularly well suited to high hazard storage applications.
Explosive Lithium-ion Batter Fire
Watch the Fire Rover tackle a battery fire in a tipping hall. Note how the exploding battery cells start three separate fires, which the operator individually suppresses (whilst avoiding the site operators in the vicinity).
STAY SAFE, STAY INFORMED
Get essential insights and updates in fire safety – straight to your inbox!